Unit not cooling house below 80 HELP ME PLEASE
It's 98 outside ... that says a lot. The gurgling is an indication that you are getting a lot of water out of the air (dehumidifying). If the unit is sized just right, or just a little too small, it may be working perfectly well.
You don't say where you are, geographically, but much to the US has an air conditioning design temperature of 95 degrees F. That means at 95 degrees, the unit will run continuously. With a 50% outside air relative humidity, it should keep the occupied space at about 75 degrees F. The more humid the air, the more the unit works on dehumidifying and less on cooling.
Give it some time, wait unti the weather breaks and see if it doesn't run just like it used to. If you chose to call a technician, have him/her take temperature readings of the condenser entering and leaving air, the suction line temperature, the liquid line temperature, the inside supply and return air temperature (dry bulb and wet bulb) as well as high and low side refrigerant pressures. Before they make ANY changes to the system (refrigerant charge) have them explain what they found wrong and make sure you understand what they are talking about. Adjusting the charge under these conditions, will mess up your operation under normal conditions.
Jul 20, 2010 |
Whirlwind FH-778 Air Conditioner