Question about Goodman CLQ36AR49 Air Conditioner
I had to disconect my wires coming from my outside unit to replace the drain pan and now I can't get the wiring right, I cant get the the compressor to kick in
Ok Let me see if this helps if not please comment back with the t-stat model and make as well. The Y terminal on the t-stat needs to be connected to the Y terminal on the heat pump board. If this does'nt fix it your thermostat may have something different going on so please send me the model and make of the t-stat. Also if you know does this unit have outside temperature sensing probes, and or an automatic defrost cycle?
Posted on Jul 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Jul 18, 2012 | Goodman Heating & Cooling
May 01, 2011 | Goodman CKL36AR36 Air Conditioner
Mar 05, 2010 | Goodman CKL60AR60 Air Conditioner
Sep 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 21, 2009 | Goodman Heating & Cooling
Jun 05, 2009 | Ruud UPMC036 Air Conditioner
Jun 02, 2009 | Goodman GMS90703BXA Heater
Aug 15, 2007 | Goodman CLQ36AR49 Air Conditioner
155 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: