Question about Heating & Cooling
There are a couple of things this may be, so will need checking to rule them out as the cause.
There is a "hot wire" sensor in the pilot flame that allows the main gas valve to come on when it gets hot.
You will need to check the output from this when cold, and when hot. It's a safety feature to prevent gas escaping when not lit.
When cold, check there is continuity in the gas valve coils. A faulty gas valve will not open. This should only be replaced by registered trades people if it is faulty.
Check the blower motor coils in the same way for continuity. If they are defective, they will not allow power to the gas valve either - or it will cause overheating.
If everything checks out ok on the boiler side, try jumping the thermostat contacts, and see if it fires up. If it does - replace the thermostat.
Thanks for using Fixya!
Posted on Jul 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 31, 2016 | Heating & Cooling
Oct 03, 2015 | Heating & Cooling
Feb 01, 2010 | Heating & Cooling
Jan 09, 2010 | Honeywell CT87B ROUND HEATING&COOLING...
Oct 20, 2009 | Heating & Cooling
Mar 16, 2009 | Goodman GMS90703BXA Heater
Oct 25, 2008 | Water Heaters
180 people viewed this question
Usually answered in minutes!