Question about DeLonghi Air Conditioners
You need to replace the thermocouple. This is a small metal rod that is positioned in such a manner that when the pilot light is burning, the flame is contacting the thermocouple. When heated by the flame, the thermocouple produces a very small amount of electricity that it sends to the gas valve. The valve then interperets the electricity as confirmation that the pilot is burning and it is safe to conitinue delivering gas. Thermocouples wear out and stop producing power. The gas valve thinks that the pilot has gone out and thus turns the gas off for safety.
Please rate my solution Fix-Ya as I put alot of effort into the detail and accuracy of my solutions.
Posted on Jul 05, 2008
Tips for a great answer:
Jan 06, 2014 | Weather King 12AJA4801AH Air Conditioner
Jul 28, 2011 | Rinnai Air Conditioners
Jun 22, 2011 | Air Conditioners
May 16, 2011 | Air Conditioners
Feb 20, 2011 | Air Conditioners
May 09, 2010 | Air Conditioners
Dec 09, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 24, 2009 | Ruud UBHC Air Conditioner
Jan 11, 2009 | Air Conditioners
Dec 26, 2008 | Air Conditioners
235 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: