Question about Carrier Heating & Cooling
SOURCE: COMPRESSOR NOT RUNNING, HOT
The high side/low side pressure equalization you describe is normal for a compressor sitting idle.
If you have an ohm meter you can check the compressor windings for opens and shorts. If your compressor is 3 phase as you state (this would be very unusual for a residential unit) you should have continuity across all 3 phases and no continuity to ground. Take the compressor out of the circuit before you check.
If the compressor does have crankcase heat, it should have been left on for at least 24 hours before starting the unit. Another cause for failure could be overcharging which could have resulted in refrigerant slugging back to the compressor.
Does the unit have any low or high pressure control safeties? If so, check them too - some have resets. You said the condenser fan ran so it's not likely the breaker blew, but check anyway and also check to make sure you have available power on all 3 phases.
Posted on May 03, 2009
eventually,cycling process is doing done if the thermostat sense the configure temperayure set up it will trigger to stop your compressor motor as well as the blower fan,blower fan independenly to you compressor.if your thingking that your compressor is tripping off,check your operating current on one line using clamp ammeter and compare to the rated current that tag on
motor compressor body,if the current flow is higher than the rated current specified on compressor motor,well problem occured it will trip your compressor,because overload protector is becoming your thermostat.but if you got same current result it was cycling process.If tripping off maybe air is present in your system call qualified ac tech, to purge out air in system.
Posted on Mar 16, 2009
The fan motor is getting hot and going off on the internal overload in the motor.
This is caused by either a low voltage, a bad capacitor, or tight or dry bearings in the motor.
To check the bearings turn the power off to the unit, then spin the fan blade if it spins freely then the bearings are ok.
To check the capacitor you will need some kind of
tester or you can buy a capacitor and replace it, that's what a lot of people do. They usually don't cost very much.
To check the voltage you will need a voltmeter and measure the volts at the unit.
Posted on Jun 09, 2009
Capacitor, dirty condencer coil causing the motor amps to run too high. But most likely worn bearing on blade side of motor causing it to pull to one side causing it to over heat and shut down. Sleve bearings should have no side play.
Posted on Jun 28, 2009
be aware that not repairing this asap that you are causing yourself more problems First I would change out the fan capacitor and see if this could be the problem. Secondly if the capacitor isn,t the problem change out the motor . By continuing to allow the system to cycle like this the compressor will take a dive on you costing more . Good Luck
Posted on Aug 04, 2009
Testimonial: "Yes, it's dual run capacitor problem. I used a stick to spin the fan blades and it starts to slowly spin and up to normal speed, so motor is good."
Tips for a great answer:
Jul 07, 2016 | Carrier Heating & Cooling
Aug 27, 2011 | Carrier Heating & Cooling
Apr 22, 2011 | Heating & Cooling
Apr 09, 2011 | Heating & Cooling
Nov 04, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Sep 20, 2009 | Carrier 38CKC042 Air Conditioner
May 09, 2009 | Carrier Heating & Cooling
May 07, 2009 | Heating & Cooling
Oct 14, 2008 | Carrier Heating & Cooling
Jun 30, 2008 | Carrier Heating & Cooling
293 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: