Question about Delfield 113.28 cu. ft. Commercial Freezer Meridian MFRI3S Stainless Steel
When freeze reaches temp. and conpresser turns off the fns should stay on but are not so the coil freezes weekly. any ideas
Check the defrost timer for operation if your unit has one. Some Delfield models have solid state controls. If your system has a timer for the defrost you can open the timer cover and turn the dial in the direction indicated by the arrow until a time peg comes up to the time of day marker. You will hear a loud click and the compressor will shut off. Defrost should take place. The inner dial of the timer will have some indication as to how long in minutes the defrost should take. If the pointer does not move while in the defrost position the timer motor is bad. Turn the dial again so the copper pointer goes past the time of day marker and the compressor should restart. Replace the timer.
Posted on Jul 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 27, 2014 | Haier RRTG21PABB 20.7 cu ft Two Door...
Sep 01, 2010 | Turbo Air 23 cu. ft. / 651 liter...
Feb 10, 2010 | Freezers
Nov 10, 2009 | Freezers
Nov 01, 2009 | Continental Freezer Wide Freezer low temp...
Sep 20, 2009 | Freezers
Jul 12, 2009 | True 49 cu. ft. / 1388 liter Commercial...
Mar 08, 2009 | Freezers
Oct 28, 2008 | Kenmore Freezer 20.3 cu. ft. Frost Free...
Jun 10, 2008 | Kenmore Freezers
231 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: