Question about Rinnai Air Conditioners
Tips for a great answer:
Check that the gas is turned on at the water heater and gas meter. Check for obstructions in
the flue outlet.
Ensure gas line, meter, and/or regulator is sized properly.
Ensure gas type and pressure is correct.
Bleed all air from gas lines.
Ensure proper Rinnai venting material was installed.
Ensure condensation collar was installed properly.
Ensure vent length is within limits.
Verify dip switches are set properly.
Ensure appliance is properly grounded.
Disconnect EZConnect™ or MSA controls to isolate the problem.
Check power supply for loose connections.
Check power supply for proper voltage and voltage drops.
Ensure flame rod wire is connected.
Check flame rod for carbon build-up.
Disconnect and reconnect all wiring harnesses on unit and PC board.
Check for DC shorts at components.
Check gas solenoid valves for open or short circuits.
Remove burner plate and inspect burner surface for condensation or debris.
The above is what #12 indicates.
No way to fix it without further hands on investigation. I seriously recommend you call a licensed plumber.
Let me know,if needed further assistance.
Hope i helped you.
Thanks for using ' Fixya ' and have a nice day!!
Jul 13, 2011 | Air Conditioners
Mar 15, 2011 | Rinnai Air Conditioners
Feb 18, 2011 | Air Conditioners
Dec 06, 2010 | Air Conditioners
Nov 01, 2010 | Rinnai Air Conditioners
Sep 06, 2010 | Air Conditioners
Jun 11, 2010 | Air Conditioners
Jul 29, 2009 | Rinnai EnergySaver 556 Air Conditioner
Jun 19, 2008 | Rinnai Air Conditioners
Jun 15, 2008 | Rinnai Air Conditioners
Nov 13, 2016 | Rinnai Air Conditioners
Sep 03, 2016 | Rinnai Air Conditioners
510 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: