Question about Carrier Heating & Cooling
A burned or pitted contactor will/can cause a unit to not run. Outside fan. Just thinking out loud. Start with low voltage check at t.stat then check outside low volt. Set t.stat to on. If fan engages at least your transformer is good. Next set calling for cool. Drop t.stat 68-70. If nothing happens go outside and with a screwdriver depress the contactor in. If fan and compressor kicks in change the contactor. If contactor is pulled in check outside fan. Remove the wires from the compressor and see if the fan will run . If it does you have eliminated start components as good. The compressor has to be check. It needs to be ohmed out. Turn off power at disconnect. Pull the cover on the compressor. Check between pins; then pins to ground. Open or infinite is good.Have you checked fuses. Like small 3-5 amp fuses
Posted on Jul 03, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2015 | Carrier Heating & Cooling
Nov 13, 2012 | Heating & Cooling
Aug 31, 2012 | Carrier Air Conditioner Accessories Air...
May 23, 2012 | Carrier 5 Ton Infinity High Efficiency...
Sep 25, 2010 | Heating & Cooling
Aug 23, 2009 | Heating & Cooling
Jul 07, 2009 | Heating & Cooling
Apr 28, 2009 | Carrier Heating & Cooling
Apr 01, 2009 | Carrier TSTATHPP 7-Day Programmable...
461 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: