Question about Carrier Air Conditioners
A burned or pitted contactor will/can cause a unit to not run. Outside fan. Just thinking out loud. Start with low voltage check at t.stat then check outside low volt. Set t.stat to on. If fan engages at least your transformer is good. Next set calling for cool. Drop t.stat 68-70. If nothing happens go outside and with a screwdriver depress the contactor in. If fan and compressor kicks in change the contactor. If contactor is pulled in check outside fan. Remove the wires from the compressor and see if the fan will run . If it does you have eliminated start components as good. The compressor has to be check. It needs to be ohmed out. Turn off power at disconnect. Pull the cover on the compressor. Check between pins; then pins to ground. Open or infinite is good.Have you checked fuses. Like small 3-5 amp fuses
Posted on Jul 03, 2008
Tips for a great answer:
Feb 14, 2015 | Carrier Air Conditioners
Nov 13, 2012 | Air Conditioners
Aug 31, 2012 | Carrier Air Conditioner Accessories Air...
Sep 25, 2010 | Air Conditioners
Jan 12, 2010 | Carrier XQB101D Air Conditioner
Aug 23, 2009 | Air Conditioners
Jul 07, 2009 | Air Conditioners
Apr 28, 2009 | Carrier Air Conditioners
Apr 01, 2009 | Carrier TSTATHPP 7-Day Programmable...
Jan 21, 2008 | Hitachi RAS-09UH Air Conditioner
Nov 28, 2016 | Carrier Air Conditioners
458 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: