Question about Heating & Cooling
My gut tells me that the indoor fan relay,24volt fuse or circuit board have gone bad, but first lets eliminate the thermostat as a problem.
1) Turn off the air handler at the disconnect switch to shut off 24v.
2) Disconnect the 24v wires from the thermostat.
3) Only connect the "R" and the "G" wires together. (Usually red and green)
4) Restore power to the air handler.
Does the fan come on? If it does than the thermostat is bad. If it does not come on then we will look closer at the other componants. Give it a shot!
Posted on Jul 09, 2008
Check the transformer. Turn t.stat to on. If the fan doesn't engage change transformer. Also discharge your capacitor and test. If micro-farads are low it is a good indicator that the capacitor is either bad or going bad. Change and crank her up...
Posted on Jul 03, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 02, 2015 | Goodman Heating & Cooling
Aug 19, 2011 | Goodman Heating & Cooling
Jan 31, 2010 | Goodman GMS90703BXA Heater
Nov 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Oct 07, 2009 | Goodman Heating & Cooling
Aug 19, 2009 | Goodman Heating & Cooling
Apr 28, 2009 | Goodman CKL60AR60 Air Conditioner
Jul 03, 2008 | Goodman CLQ36AR49 Air Conditioner
Jun 26, 2008 | Goodman CKL60AR60 Air Conditioner
1,704 people viewed this question
Usually answered in minutes!