Question about Dometic Rooftop RV Air Conditioner
If this is a wall thermostat controlled unit, then check to make sure that you have power coming from the yellow wire on the thermostat when it is placed in the Cool/Auto High mode. If you do not have power at the yellow wire, then you have a bad thermostat. If you do have power, then remove the control unit from the inside of the AC and see if you have power at the Y terminal there. If so, when you turn the thermostat to cool, can you hear a relay clicking in the box? If not, then you have a bad control box. If the relay is clicking, you need to check the power at the compressor relay on the board. It has a black wire to one side and a purple (or blue) wire on the outgoing side. Check to see if you have 120V on the blue wire when the tstat is set to High/Cool. If not, then you need to bypass the freeze switch to make sure that is not the problem. If you do, then you need to go upstairs and check the start capacitor for OK. It is located in the side compartment of the upper unit, it has a small black relay on the top called a PTCR. These often burn out and will cause the compressor not to work. If that is fine, then you go to the top of the compressor to the thermal overload switch. See if you have power at both sides, if so, then you have a bad compressor. If not, then the overload switch is open and not allowing power to the compressor.
Posted on Jul 04, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2017 | Heating & Cooling
Jan 08, 2017 | Heating & Cooling
Jan 07, 2017 | Heating & Cooling
Jan 05, 2017 | GE Heating & Cooling
Jan 03, 2017 | Royal Heating & Cooling
Jan 03, 2017 | Heating & Cooling
Dec 27, 2014 | Heating & Cooling
Nov 07, 2014 | Heating & Cooling
Jan 01, 2014 | Williams (5009622) Ceramic Gas Wall...
Jul 26, 2008 | Friedrich QuietMaster Electronic SS12J30D...
69 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: