Question about Carrier Heating & Cooling
I have seen this before when there is an obstruction in the evaporator coil metering device. This causes the compressor to struggle moving the Puron. After the Puron has been recovered make sure that they do a complete check of the metering device and check for other obstructions. When they are done checking they must do a proper vacuum to remove any non condensables like water condensation. Finally they should have installed both a liquid and suction filter dryer to reduce any dirt and stuff. The only other options are unlikely, as we will assume that the last company installed the correct (new) compressor and that they did not do a hack job.
On a happier note, the compressor should still be under the 10 year parts warranty!
Posted on Jul 01, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 28, 2015 | LG Cell Phones
Feb 26, 2013 | Heating & Cooling
Aug 31, 2010 | Carrier Heating & Cooling
Aug 08, 2010 | Carrier 38CKC024 Air Conditioner
Jun 26, 2010 | GE Profile PFS22 33" Artica French Door...
May 16, 2009 | Carrier 38CKC036 Air Conditioner
Aug 01, 2008 | Carrier 38CKC036 Air Conditioner
537 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: