Question about Coleman Heating & Cooling
You may have a low pressure or high pressure switch tripping out the board as well. You might try cleaning both the indoor (evaporator) coil and the outdoor (condensing) coil. Be sure to turn off the power source before servicing this.
Posted on Jul 01, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 01, 2016 | Coleman Heating & Cooling
Dec 22, 2015 | Coleman Electrical Supplies
Feb 12, 2015 | Coleman Heating & Cooling
May 25, 2014 | Coleman Mach III Air Conditioner
Aug 13, 2012 | Coleman Mach 15 Air Conditioner
Oct 01, 2010 | Mitsubishi VS-70707 70" Rear Projection...
Jun 09, 2010 | Kenmore 55612 / 55614 / 5561 / 655619 Side...
May 01, 2010 | Coleman Powermate Powermate 5000W...
Oct 01, 2009 | Coleman Mach III Air Conditioner
May 04, 2008 | Heating & Cooling
Jan 06, 2018 | Coleman Heating & Cooling
Dec 10, 2017 | Coleman Heating & Cooling
82 people viewed this question
Usually answered in minutes!