Question about Heating & Cooling
It sounds as if it is tripping on high pressure. This can be directly related to outdoor temp. Most residential a/c units will run a maximum capacity over 95 degrees. The compressor should not be shutting down though.
The best thing you can do, (short of hiring the company to come back), is making certain that the outdoor coil is free of debris. You should be able to see light through the coil fins. Also make sure that the indoor filter has been changed. Finally (with the outdoor breaker off) look at the fan blades on the exhaust motor. If they look cracked or uncentered then they could be your problem. Any further service should be done by a licensed technician because the other options are highly technical. I will list some of them here:
blocked or failed metering device (no or very low suction/high head)
kinked or obstructed line set (irregular pressures)
too much refrigerant (irregular pressures)
over amping exhaust fan motor (sometimes intermittent)
unmatched condenser to evaporator (corrected by Heat gain calc)
weak or failing capacitor (measured using special fluke style meter)
Posted on Jun 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 21, 2015 | Heating & Cooling
Mar 04, 2015 | Amana PTH123B25AJ Heat Pump Air...
Feb 23, 2010 | Heating & Cooling
Feb 23, 2010 | Dometic Rooftop RV Air Conditioner
Jan 13, 2010 | Heating & Cooling
Jan 02, 2010 | Ruud UBHC Air Conditioner
Jun 01, 2009 | Ruud UAMB Air Conditioner
Apr 06, 2009 | Amana PTC153B50AJ Electric Heat Air...
Dec 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
Feb 26, 2017 | Heating & Cooling
112 people viewed this question
Usually answered in minutes!