Question about Carrier Heating & Cooling
Air conditioning requires 400 cfm (cubic feet per minute) per ton of cooling so your old 2.5 ton system would have required 1000 cfm and your new 3 ton requires 1200 cfm. This is not a big change, but if your ductwork is too small it could cause problems. The best way to check to see if airflow is the problem is to check the temperature of the air going in to the system and then check it when it comes out. Take a temp reading with a reliable digital thermometer at the return grill ( the vent that is physically the closest to the furnace that is sucking air in). Then take a temperature reading at the vent that is physically closest to the furnace and that is blowing air out. The target range is for the air coming out to be 18-22 deg F colder that the air going in. If the air is coming out is more than 22 deg colder then there is not enough air moving through the system. If the air is coming out is less than 18 deg colder then the problem is with the system. Potential problems range from improper refrigerant charge or incorrect refrigerant metering to wrong coil/volume ratio which is essentially mis-matched equipment. It sounds to me like you have a company that doesn't really have much of a clue what they are doing. When the company I work for changes equipment in a house to a larger capacity, we always check the ductwork and do the math ahead of time to make sure that things will work rather that throwing things at problems later. Also, when you check your temps turn the system on and allow it to run for about 10-15 min first so that everything has a chance to stabilize and the ductwork has a chance to cool down.
Posted on Jun 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 27, 2014 | Heating & Cooling
on Dec 24, 2009 | Heating & Cooling
on Dec 06, 2009 | Heating & Cooling
Jun 27, 2012 | 1983 Cadillac DeVille
Mar 01, 2017 | Heating & Cooling
Jun 11, 2010 | Carrier 38CKC036 Air Conditioner
Feb 22, 2010 | 1983 Chevrolet Silverado
Jan 26, 2010 | Rinnai Digital Remote Water Heater Control...
136 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: