Question about Heating & Cooling
Air conditioner probably has a failed run capacitor inside the unit. Check all circuit breakers and/or fuses first.
Posted on Jun 30, 2008
Unit fan comes on unit runs fan shows that it's running but not getting cold. Second unit comes on no problem getting cold.
Posted on Apr 20, 2009
Just because the big one is cold and the small one is warm,Doesn't tell you if the system is properly charged or properly working.It is true that the big line will be cold and have condensation on it and the small one will be hot and dry,But this occurs in a wide pressure range,so the system could still be improperly charged.The charge in the system is based on the ambient temperature,The size of the system,The line footage,Etc............ So without a set of gauges and the ambient temperature,You can't really check anything but whether or not the unit comes on.
Posted on May 20, 2009
SOURCE: air conditioner
Turn off unit supply and check the blower wheel inside the indoor unit by rotating it manually by your finger if the blower wheel rotates freely then there is something wrong with your fan motor or fan motor capacitor. But if the blower wheel is not rotating freely try to check the fan motor for lubrication or some bushing dried of and no oil
Posted on Dec 31, 2007
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 02, 2014 | Comfortmaker Heating & Cooling
Jun 17, 2013 | Heating & Cooling
Jun 24, 2010 | Heating & Cooling
Apr 04, 2010 | Ruud UBHC Air Conditioner
Sep 27, 2009 | Ruud UBHC Air Conditioner
Aug 10, 2009 | Heating & Cooling
May 01, 2009 | Kenmore 72187 Air Conditioner
Aug 25, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jun 16, 2007 | Weather King 12AJA4801AH Air Conditioner
Jan 18, 2017 | Williams Heating & Cooling
664 people viewed this question
Usually answered in minutes!