Question about Carrier Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Make sure a back draft in the flue is not happening. Wind can blow it out until the flue heats up. The flame sensor may not be close enough to the burner flame. It may be weak and need to be replaced or if its an optical one it may be dirty and not see the flame very well. Its not wasting much gas but it puts extra wear and tear on the gas controls, is noisy, and, as you said, blows cold drafty air. A gas control system that has issues of any kind is not real safe. It needs to get fixed.
Posted on Jan 08, 2009
the cap is usually next to the contactor on the outside unit and most are dual caos one terminal for fan marked "F" and one marked "H" for hermetic compressor and will have 2 mfd ratings at 370volt or 440 volt a.c. operation
Posted on Sep 26, 2009
SOURCE: Carrier furnace fan works in
First take off the thermostat cover and turn off power to unit jump the R,G Y wires at the thermostat subbase with power back on, if the fan starts up then the thermostat is bad and must be replaced. If it still does not start then the relay on the control board is bad and must be replaced.
Posted on Jun 25, 2011
Tips for a great answer:
Jun 16, 2017 | Carrier Heating & Cooling
Apr 30, 2016 | Carrier Heating & Cooling
Jul 20, 2015 | Heating & Cooling
Mar 22, 2015 | Carrier Heating & Cooling
Feb 18, 2015 | Carrier Heating & Cooling
Jun 26, 2011 | Carrier 38CKC042 Air Conditioner
Sep 27, 2010 | Carrier 36KCARMS Air Conditioner
Jan 01, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Apr 20, 2009 | Carrier Heating & Cooling
Aug 17, 2008 | Carrier 38BRC048 Air Conditioner
68 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: