- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Dear friend, find below symbols for mode setting. For cool keep minimum 3 degree less than room temp and heat keep minimum 3 degree higher than room temp. Dry mode will help you only in wintertime. Thanks.
Now symbols: 1. fan leaves - Fan only 2. Rain drop- Dry mode 3. Snow flake-Cool mode 4. Sun- Heat 5. A or AU- Auto mode.Helpful?
Toget proper heat, keep your temp setting at 30+ degree and also mode in "heat"position. If still no heat, check your heating sensor for closed circuit by anOHMs metre.It it's with RV, check power to RV.If it's with heatingelement check power to element. If power is there but still no heat meanselement defective. Replace new heating element. Thanks.
To get proper cool, keep the tips as follows: 1. Check air filter is cleaned. 2. Check indoor coil is cleaned. 3. Checkindoor blower motor is working. 4. Keep in cool mode. 5. Set temp minimum 3degrees less than room temp.6.Check compressor is working with correctpressure. Thanks. Helpful?
Sounds like there is a problem with your unit. The cooling tower doesn't have anything to do with the compressor other that the delivery of water to your heat pump. The compressor is probably shutting off on a low pressure because the water is cooler than in summer. I think the heat pump you have is low on charge or has a defunct TXV.
I know it has been at least a year since your post. I am answering the post to terminate FixYa site activity on the post.
Remove the front cover. Check the routing of the temp sensor wire. It should go from the bottom of the control panel to the plastic clip in the evaporator coils. If it is touching the eavporator coils it will sense the refrigerant temp and cycle off early. If the unit is freezing up there is a restriction in the coolant lines and usually will require the coolant system be purged of foreign internal debris.
I have a fairly new Haier Air Condition that I bought last year, it has been working good up until last night. I keep this one in my bedroom and put it on every night since the summer. Last night I woke up very warm, the temp reading was 75 the AC did nothing but blow out just air. I threw away the booklet on it because I've had no problem up until now. Does anyone know how I can make it cold again. HELP!!!!