Question about Carrier 38CKC036 Air Conditioner
Two days ago, the fan stoped working. I don't smell anything, when I placed my hands on the unit, I can feel there is some electricity sensation and sometimes I can hear some noise for 2 secs.
I spoke to a friend and he said it may de the condensation system. Unit is from 2004, does it have still warranty on it?
It sounds like it is the run capacitor on the fan motor is defective.
Typically when this fails, the motor will buzz, and get hot - without rotating. When it gets too warm, the temperature cut-out will shut it off untill it cools down.
Try replacing this with one of a similar value or a genuine part.
I don't think it is under warranty after this time.
Posted on Jun 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 18, 2012 | Carrier 38CKC036 Air Conditioner
Sep 10, 2011 | Carrier 52PQ307 Wall/Window Air...
Jun 20, 2011 | Carrier 38CKC036 Air Conditioner
Dec 31, 2010 | 2000 Ford Focus
Jun 10, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 17, 2009 | Hunter 52" Ceiling Fan With Light And...
Sep 05, 2009 | Carrier 38CKC042 Air Conditioner
Jun 10, 2009 | Carrier 38CKC036 Air Conditioner
Jan 03, 2009 | 1999 Volkswagen Beetle
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
257 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: