Question about Heating & Cooling
Most likely the cause is that the furnace is firing too hot. When a furnace is installed and set up, the manifold gas pressure and fan speed has to be set by the technician so that the temperature rise through the furnace is a maximum of 50 deg F (i.e. if air enters the furnace at 68 deg F it come out no hotter than 118). The target temperature rise on any gas furnace is anywhere between 30 and 50 deg F. If the furnace runs too hot, either the manifold gas pressure must be turned down or the fan speed must be turned up to keep in this range.
Posted on Jun 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2017 | Gibson Heating & Cooling
Jan 28, 2014 | Goodman Manufacturing Goodman 60,000 btu...
Jun 04, 2010 | Goodman GMS90703BXA Heater
Mar 09, 2010 | Heating & Cooling
Feb 13, 2010 | Heating & Cooling
Feb 11, 2010 | Heating & Cooling
Jan 30, 2010 | Heating & Cooling
Mar 31, 2009 | Coleman Propane Forced Air Heater...
Mar 28, 2009 | Heating & Cooling
Jan 08, 2009 | Heating & Cooling
211 people viewed this question
Usually answered in minutes!