Question about Heating & Cooling
I had to replace both hi limit sensors in mine. The sockets that they fit into has a plug inside that corrodes and allows clorine water to escape. I had to put the plugs in with auto gasket sealant around threads only. This solution helps but the sensors should be inspected now and then for corrosion. Lithium grease on electrical conectors on the bottom of sensor helps to. This area is attacked by corrosion big time along with top. (winterizing) On low pressure switch inside the heater the copper tube must be undone on switch or undrained clorine will clog up lower tube with corrosion. This blocks low pressure switch from working. Then you have to cut small piece off and redo the tubing. Been there done that. For the most part the Laars hasnt been a bad pool heater but the hi limit sensors along with the plugs could have been engineered better. Good luck and watch the ph...StLouis
Posted on Aug 28, 2008
Posted on Jul 17, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 17, 2012 | Jandy Laars Lt 250,000 Btu Heater
Jul 08, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 29, 2010 | Teledyne Laars Laars Lx Pool Heater /...
Jul 16, 2010 | Jandy Laars LX Pool Heater / 400,000 BTU /...
Jul 14, 2010 | Jandy Laars LX Pool Heater / 400,000 BTU /...
May 18, 2010 | Jandy 131K BTU LAARS AIR ENERGY HEAT PUMP...
Mar 05, 2010 | Jandy Laars LX Pool Heater / 400,000 BTU /...
177 people viewed this question
Usually answered in minutes!