Question about Heating & Cooling
This could be 2 issues. 1 being a simple issue and the other requiring service.
Make sure you have the thermostat on cool and not Fan.
If the thermostat was on cool and not fan, It sounds like the freeon level is low in your system. This will cause the air to not be cold. You will need to contact your local heating and air conditioning shop and have them take a look at this. You may be low on freeon because of a leak in your system also. It is recommended you get your system checked and tuned up every year. The cost of this is usually between $50 and $90. It is a good idea because they can catch problems early on before they become larger problems. It also will also keep your central air system running efficiently and use less power compared to a system that has not been maintained. Keep me posted and if you found this helpful please rate accordingly.
Thanks - Tech101
Posted on Jun 27, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Can you tell if your outside unit is running (the fan and compressor)? Sometimes it is hard to hear the compressor for the fan. If they are running then you possibly have a low refrigerant charge and need to have some added. Refrigerant pressures and temps can be checked to verify this. If they are not running then you need to find out why. If both the fan and compressor are not running then first make sure all the breakers and disconnects are closed. Then a bad contactor or capacitor could be the problem. If its just the compressor that's not running then it could still be the capacitor or maybe the compressor.
Posted on Apr 29, 2010
Testimonial: "Thanks, this is very helpful."
Tips for a great answer:
Feb 14, 2016 | Heating & Cooling
Sep 10, 2008 | Amana Heating & Cooling
Jun 17, 2015 | LG L1204R Air Conditioner
May 27, 2014 | Mitsubishi MSH09TW Air Conditioner
Jul 15, 2011 | Intertherm Heating & Cooling
Jul 08, 2010 | Ruud UAPA042 Air Conditioner
Jun 01, 2010 | Goodman GMS90703BXA Heater
Aug 09, 2009 | Carrier Heating & Cooling
145 people viewed this question
Usually answered in minutes!