Question about Heating & Cooling
It could also be the contactor; basically an electrically-controlled switch that in turn controls the compressor and the condenser fan. If it's a 220 volt motor, and one side of the contactor has very high resistance, it'll be seeing 110 volts instead, basically causing it to either run at roughly half speed or just sit and stutter, or other weird random stuff. Depending on the contactor design, you might be able to get an emery board (yes, for fingernails--they work great!) between the contacts and lightly buff them. Of course make sure the breaker that feeds the unit is turned off and tagged out first! Barring that, I'd check - in order - the capacitor and the fan motor itself.
And just to rule it out, go through and make sure that each end of every wire is firmly attached to whatever it's attached to. Over time those quick-disconnect connectors can work loose, causing again all manner of random stuff to happen. If you find a loose one, you can probably use a pair of pliers and gently squeeze the connector tight again. Of course make sure the breaker is off and tagged before you stick your fingers in there...220 volts WILL send you flying. Or just kill you.
The 60Hz shuffle is no fun at all. Be safe.
Posted on Jul 28, 2008
I am not sure what kind of air conditioner that this is. If it is a split system A/C then the outdoor exhaust fan should always spin at the same RPM. So if your fan is spinning slowly and humming, it is probably the run capacitor. I will bet that the capacitor is leaking oil or ballooned out. It most cases this is a combination capacitor that runs both the compressor and the exhaust fan. It should be replaced. This usually happens as a result of excess heat or normal wear and tear. After it is replaced it will be a good idea to have the system checked out to make sure the condenser is exhausting the heat correctly.
Posted on Jun 27, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 30, 2016 | Amana PTH153B50AJ Heat Pump Air...
Feb 23, 2014 | ComfortStar CHH012CD-13B Wall Mounted Mini...
Sep 30, 2013 | Dometic Rooftop RV Air Conditioner
Jan 19, 2012 | 2002 Chevrolet Malibu
Jan 11, 2011 | Ruud Heating & Cooling
Jan 03, 2011 | Heating & Cooling
Dec 20, 2010 | Heating & Cooling
Nov 25, 2010 | Heating & Cooling
Jan 05, 2010 | Heating & Cooling
Mar 28, 2009 | Carrier Heating & Cooling
May 22, 2017 | Heating & Cooling
140 people viewed this question
Usually answered in minutes!