Question about Weather King 10AJA2501AH Air Conditioner
I have a Honeywell T87F thermastat that is turning the air conditioner on (you can hear it) but not the house fan. I can turn the fan on via a button in the basement but auto does not work. This just started acting up last night.
If you have a voltmeter that checks capacitance, check the capacitor ( silver looking battery) that is mounted on the side of the blower housing in the furnace. You need to take the wires off!! A bad Cap will slow down the fan and if its blown/dead the fan will not run.
If youre more than 1 MFD off the rating stamped on the capacitor, Replace it.
Posted on Jul 08, 2008
Ok heres a test i want you to do carefully remove the thermostat cover and you will see the 3 wires one is red the other one is yellow and a green one turn off the thermostat and remove the wire from thermostat labeled G and carefully touch it on the R terminal if fan turns on, thermostat is defective if it dosen't turn on there should be a fan section on control board that's defective
Posted on Jun 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 21, 2016 | Honeywell Heating & Cooling
Aug 16, 2011 | Heating & Cooling
Aug 02, 2010 | Dometic 57915531 Air Conditioner
Jul 04, 2010 | Honeywell ER150B Air Conditioner
Jun 23, 2010 | Amana PBC101A00A Air Conditioner
Oct 07, 2009 | Honeywell Heating & Cooling
Nov 22, 2008 | Honeywell Heating & Cooling
Jun 09, 2008 | Honeywell Heating & Cooling
332 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: