Question about Heating & Cooling
Make sure that the outdoor unit is on. If it is on, then check to hear if both the big black compressor is running as well as the fan. If both are running then feel the fat copper pipe that comes out of the unit. If it is not cold and sweaty then your system is probably very low on refrigerant. If the line shows evidence of icing, it could still be a little low. Although icing can be the result of 4or 5 other problems as well.
Posted on Jun 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 01, 2014 | Quasar HQ2051TH Air Conditioner
Apr 22, 2012 | Heating & Cooling
Jun 07, 2011 | Goodman Heating & Cooling
Aug 14, 2010 | Honeywell Heating & Cooling
Jul 06, 2010 | Heating & Cooling
Jun 09, 2010 | Heating & Cooling
Mar 18, 2010 | LG Heating & Cooling
Aug 22, 2009 | Heating & Cooling
Jul 03, 2008 | Heating & Cooling
105 people viewed this question
Usually answered in minutes!