Question about Carrier 36KCARMS Air Conditioner
Our daughter and son-in-law have a Carrier air conditioner. They can't seem to get the air conditioner to cool down the house. The main 'black' pipe coming from the air conditioner to the inside furnace also has a small copper tube running along side of it. The copper tube is very warm, almost hot to the touch. The same copper tube on my air conditioner is room temperature, not warm at all.
Could the problem be with this tubing? What fluid runs through this copper tubing?
Any advice would be appreciated.
email - firstname.lastname@example.org
This tubbing carries the refrigerant. The small line is flowing to their inside air handler. If the line is hot it is an indication that the outside unit is not able to release the heat. The most common reason is that the coil (looks like a car radiator) is dirty or plugged. This can be cleaned with a brush or sometimes a garden hose. They do make acid type cleaners for doing this, but the use of the acids are restricted in some areas.
By the way the other black pipe should have a larger copper line behind the black insulation. That line should be cold and sweaty like a nice glass of ice tea:)
Posted on Jun 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 30, 2012 | Carrier 38CKC024 Air Conditioner
Jan 05, 2012 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 20, 2010 | Carrier 38CKC024 Air Conditioner
Aug 09, 2009 | Carrier Heating & Cooling
May 21, 2009 | Carrier Heating & Cooling
Sep 01, 2008 | Carrier Heating & Cooling
Jul 19, 2008 | Haier Energy Star ESA3183 Air Conditioner
May 26, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
338 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: