Question about Goodman Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You stated capasitor was checked . if cap. is ok sometimes start terminal wire will burn into at compressor or you may have a loose connection causing a voltage drop (more than 10%).If both check ok try a hard start kit. Who knows it might start. good luck
Posted on Jan 20, 2008
Bad bearings on the motor or check the fan rotations . Air should always blow out the top and **** in through the sides or coils.!... Thank-you-very-much!
Posted on Aug 25, 2008
Make sure ALL moisture and noncondensables are evacuated while the system is down.I would have the line flushed to remove all remnants of burnout.Actually with the age of the unit and amount that needs repaired I would change the unit out to a 410a system and start over.
Posted on Nov 02, 2008
It sounds like your defrost board failed. You will need a tech to replace it. With that model it may have a parts warranty but you pay labor(?)
Posted on Jan 18, 2009
SOURCE: Replaced my 5-year old 3-ton 12 SEER Goodman outside condensing unit with an older 3-ton RUDD condensing unit because of lack of funds. Now the compressor has gone out on the RUDD. Is it better to rep
A new unit will be 13+ seer unless you can find someone that has replaced a compressor or has one left over from pre 2006 stock. Our wise Government with all its resources decided that we aren't smart enough to turn off the lights to save energy, so they chose to end the med and low price lines. And the same bunch of smart ones decided that now R22 because of its chlorien content being bad for the air (5% of what R12 was) so we have R410A and others that no one knows how much cancer or daMAGE THEY WILL DO OVER TIME. So now if you replace your AC unit out side with a new one be sure its compatable with the refrigerant inside and beware soem manufacturers wont stand up to full warranty if you dont buy an indoor coil and rerplace it too.
We get what we deserve in Washington DC and if our guy didnt support this stuf too many other folks guys did. We just dont talk about it enough. AND WE SHOULD. But then again you like me are probably RITCH. So we have to give up our wealth to the government so they can redistribute it and buy more votes. And we can stay working too much to talk about it.
Just burns my back side like a 4 foot flame.
Read tween the politics and you'll get my recomendation.
Buy your self a compressor and get someone qualified to install it or see if the old goodman one will interchange easily.
Posted on May 12, 2009
Tips for a great answer:
Jul 30, 2014 | Goodman Manufacturing Goodman GSX130481...
Jul 06, 2014 | Goodman CLQ36AR49 Air Conditioner
Sep 27, 2012 | Goodman Manufacturing Goodman GSC130301...
Jul 08, 2012 | Goodman CKL49AR49 Air Conditioner
Aug 12, 2011 | Goodman CKL42AR42 Air Conditioner
Jul 27, 2010 | Goodman CKL60AR60 Air Conditioner
Aug 16, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 30, 2009 | Goodman CKL60AR60 Air Conditioner
Apr 23, 2009 | Goodman CKL42AR42 Air Conditioner
862 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: