Question about Weather King Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: replace contactor
On single phase your incoming power lines go to L-1 & L-2, the lines to the compressor go to T-1 & T-2. With A/C current it does not matter which one goes to which side as long as the line goes to the L side and the compressor power lines go to the T side. As long as the coil voltage is correct any contactor will replace the original.
Posted on May 29, 2008
SOURCE: warranty on compressor
The actual age of your unit can be determined by the serial number. Based on the age indicated there they can tell you if the warranty is still valid. Your local Rheem/weather king dealer can do this for you. Most compressor warranties are either 5 or 10 years. Good Luck!
Posted on Jul 03, 2008
SOURCE: compressor will not start.
sounds like the compressor is shorted out, or froze up. the 1 second buzz you hear is the compressors internal overload protector kickin in and shutting the comp. down. its a self resetting circuit breaker. for the most part, the compressor is out and needs replaced.
Posted on Sep 02, 2009
SOURCE: the compressor is not starting.
Check the capacitor. (The thing that looks like a big battery). If it is bulged out on the sides it is shorted. The compressor could be "locked" up which is the worse case.
Posted on Apr 11, 2011
Testimonial: "Capacitor was my next guess. I measured ohms per google and they were correct. I will get a capacitor tomorrow. If no, call AC guys"
Tips for a great answer:
Sep 01, 2013 | Ruud Heating & Cooling
Jul 27, 2012 | Ruud UAMB Air Conditioner
Apr 14, 2011 | Goodman HDC24WMC24 Air Conditioner
Nov 10, 2010 | Heating & Cooling
Mar 13, 2010 | Amana 22.6 cu. ft. Side-By-Side...
Oct 10, 2009 | Heating & Cooling
Aug 23, 2009 | Heating & Cooling
May 15, 2009 | Goodman CKL60AR60 Air Conditioner
May 29, 2008 | Ruud Central System Air Conditioner
117 people viewed this question
Usually answered in minutes!