Question about Intertherm Heating & Cooling
Most likely a failed run capacitor in the outdoor unit. The unit either has two separate run capacitors; one for the outdoor fan and one for the compressor. Or it may have one dual run capacitor which is the two capacitors built into one casing. Usually either a grey or silver cylinder with terminal connections on one end. If you intend to replace, make sure the power is off first by pulling the disconnect or turning off the breaker. Mark all wires and make sure they get back to the same terminal on the new capacitor. Capacitors are rated by their capacity (go figure) the new cap must match the old cap exactly on the uF or MFD (called micro-farads) rating. Voltage rating on the capacitor must be 370v or higher (most new caps are 440v rated). If you are not completely comfortable doing this yourself, a qualified HVAC service company can take care of the problem for you.
Posted on Jun 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 17, 2016 | Intertherm Heating & Cooling
Feb 14, 2012 | Heating & Cooling
Aug 30, 2011 | Ruud Heating & Cooling
Aug 05, 2011 | Heating & Cooling
May 28, 2010 | Coleman Heating & Cooling
Nov 03, 2009 | Intertherm P3RC-030K Air Conditioner
May 26, 2009 | Goodman CPLE24-1 Air Conditioner
Apr 11, 2009 | Heating & Cooling
Apr 04, 2009 | Heating & Cooling
May 06, 2008 | Weather King 10AJA2501AH Air Conditioner
160 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: