Question about Carrier 38CKC042 Air Conditioner
Trying to replace contactor, electrical hook-ups don't match from old part to relacement.....HELP!
Double check that the new contactor has the same electrical ratings on it. My guess is that the coil should be 24v while the relay should be able to carry the same amperage at 220v.
First shut off the breaker and disconnect switch for the furnace and outdoor condenser and call a licensed HVAC contractor:)
If you are determined to do it yourself, Then read the schematics first. Be aware, if you mis wire the system you may cause more damage than you have now. Not to mention your personal safety is at risk.
I am basing this on the most common style contactor found in my area.
The main relay side should be labeled. (eg. L1,L2-T1, T2). These should match exactly like the old one. L1 and L2 are the incoming power. T1 and T2 are the power leaving the contactor. All the 220v wires should correspond to one of these four terminals either by screwing them down or fitting the spade connectors together.
Usually the 24v wires will plug onto the coil (near the bottom, left and/or right sides of the contactor) silver spade connectors.
(STEP 1.) Leave all Wires Connected to your Old Contactor.
(STEP 2.) Remove the two mounting screws that hold the Old Contactor to the Air Conditioners casing.
(STEP 3.) Now Install the New Contactor to the old contactors existing location using the Same two Screws.
(STEP 4.) Now take Off one wire at a time from your old Contactor and Install each wire one at a time to the proper location on the new Contactor.
Posted on Jun 25, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 11, 2017 | Coleman Heating & Cooling
Oct 24, 2013 | Carrier Heating & Cooling
Sep 23, 2011 | Carrier 50TJ028 Rooftop Electric Cool Air...
Feb 04, 2011 | Ruud Matching Split Air Conditioner
Jun 21, 2010 | Carrier 38CKC042 Air Conditioner
Jan 12, 2010 | Carrier 38CKC042 Air Conditioner
Jan 11, 2010 | Heating & Cooling
May 11, 2009 | Carrier 38CKC036 Air Conditioner
Jul 25, 2008 | Goodman Heating & Cooling
309 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: