Compressor want come on
Here is what to do . Pull out or turn off Electrical disconnect behind unit . Carefully remove panel covering controls in unit . Note most units have a flat panel with a few screws, but some GE units have a welded metal box on top of unit which needs to be removed. After exposing controls. replace or turn on disconnect. Then take a plastic handled screwdriver and push in on center of contactor (boxlike part with a lot of wires hooked ) If the compressor now comes on release contactor , and check for 24 Volts AC at base of contactor where thermostat (small wires that run on outside of black refrigerant line ) with thermostat on and calling for cool you should measure 24 to 28 volts . If voltage is present replace contactor after disconnecting from power. If no voltage go inside , remove cover from thermostat, and check for 24 volts between red ( R) and yellow (Y ) terminals on thermostat , If voltage is present , replace thermostat , no voltage check voltage in heater / air handler if you have voltage at air handler , replace thermostat wire from heater to thermostat / if no voltage check for blown fuse in heater , this should be either an inline fuse or an automotive type fuse plugged into circuit board (with power to heater disconnected check broken wire or black mark in fuse when held up to light. If fuse good turn on power to heater and check for 230v to one side of transformer, if you get voltage to Primary (incoming side ) of transformer, check output side of transformer for 24 - 28 volts. If transformer shows input but no output replace transformer after turning power off. If you heard a buzzing or grinding noise , when pushing in contactor , but compressor didn't start look at run capacitor (this is round or oval shaped object with wires going to contactor and compressor ) Looking at area where wires plug this should be a flat surface , if it looks domed shaped or bulging out , it is blown and needs replaced , use same mfd rating and 440 Volts to be on safe side. / If there was no noise from compressor when contactor was pushed in , put your hand on top of compressor (black object in center of unit ) If hot , allow to cool for at least three hours with power to unit turned off and retest . If compressor comes on after cooling , check for bad fan motor in outside unit (it may make a squealing or wining noise and stop runing for a while , also check for / clean outdoor coils
Hope this helps .
Oct 04, 2014 |
Carrier Comfort 3.0 Ton 13 Seer Ac Only...