Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Make sure that gas control knob is set to ON (counterclockwise).
Make sure that ON/OFF switch is ON.
Check that temperature setting is high enough to call for heat.
Make sure pool pump is running and water is flowing to unit.
If not above there is a diagnostic procedure on page 33 of manual at:
Posted on May 30, 2009
SOURCE: pool heater wont fire up
Its just after 1 am here as well, Ontario Canada. Yes, you have to remove the front lower panel by raising it then pulling out at the bottom. Then compare the valve you have with the 2 in the picture on pg 5. If it is easier, you can have your husband call me while doing this and I can talk him through it. My contact information is located on the main page of my company website www.emshvac.com
Posted on Jun 23, 2009
What you probably need, you may be able to install yourself and save some$$$. It's call a thermocouple. It's a long thin tube that has a probe bulb at one end and snakes it's way back to the gas regulator.14 years is plenty of service to get from one of these.Don't laugh, but often times you can find a good one on anold gas heater in the metal pile of your local dump. It's worth a peek. If not get one of your heat and cool contractor friends drunk, then ask him to pick one up at the gas company. Town laws vary greatly from town to town. Here in Provincetown we can hardly change a light bulb without a permit...lol. Good luck, I have faith in you. Thanks Dana.
Posted on Aug 21, 2009
Tips for a great answer:
May 20, 2015 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jun 01, 2014 | Raypak Pool & Spa
Jul 19, 2011 | Raypak Versa 55k Btu Natural Gas Millivolt...
Jun 19, 2010 | Raypak Versa 130,000 Btu Above Ground...
Jul 11, 2009 | Raypak Versa 130,000 Btu Above Ground...
May 18, 2009 | Raypak Free Hydraulic Lift Gate Delivery -...
Jan 21, 2018 | Heating & Cooling
210 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: