Question about Honeywell Heating & Cooling
Your red wire from the old R terminal goes to both the R and Rc terminal on the new stat. Other wires from old stat move to same terminal on new stat. You will not have any connections to the B or O terminal. Sounds like you probably already have it hooked up right though. This thermostat is what we call a power-stealing thermostat. It "steals" is power by running a trickle current to the transformer from the R terminal back through the W terminal. This meathod requires a standard resistive type thermal relay for the heating system. If you have an electronic type circuit board, many times they do not provide the proper type of connection for the thermostat to "steal" the necessary amount of power to run on. This is solved by installing a resistor from W to C in the furnace. If you have a standard electric furnace with thermal relays, then the problem is most likly the thermostat
Posted on Jun 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 26, 2013 | Honeywell Heating & Cooling
Sep 30, 2010 | Honeywell Focus 6300B 5-2 Days...
Sep 25, 2010 | Heating & Cooling
May 31, 2010 | Honeywell Programmable Thermostat Heater
Jan 21, 2010 | Honeywell Programmable Thermostat Heater
Jul 08, 2009 | Honeywell Heat/Cool Thermostat
Jan 10, 2009 | Honeywell Focus 6300B 5-2 Days...
Dec 20, 2008 | Honeywell Electronic Programmable...
Dec 11, 2008 | Honeywell CT87B ROUND HEATING&COOLING...
May 24, 2017 | Honeywell Heating & Cooling
397 people viewed this question
Usually answered in minutes!