Question about Frigidaire Heating & Cooling
The thermal relay that controls the elements is probably welded shut. If elements come on and turn off with the a/c then something is wrong in the low voltage wiring. You will need an amp clamp meter to see which element(s) are running, check both wires going to each element as an element can break and short to ground causing it to run somewhat. Once you find what element(s) are running, trace the wires back to the sequencer. Check the bottom terminals on the sequencer for 24v. If you have 24v at sequencer, you have a problem with the low voltage wiring, if not then the sequencer has failed and must be replaced.
Posted on Jun 20, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 16, 2014 | Heating & Cooling
May 08, 2014 | Goodman Manufacturing Goodman GSC130421...
May 20, 2012 | Heating & Cooling
Jul 18, 2011 | Ruud UBHC Air Conditioner
Feb 09, 2011 | Amana Heating & Cooling
Apr 30, 2009 | Heating & Cooling
Feb 12, 2009 | Ruud UAMB Air Conditioner
Oct 26, 2008 | Heating & Cooling
53 people viewed this question
Usually answered in minutes!