Question about Hitachi RAS-09UH Air Conditioner
Have a Hitachi Soleus split unit KFR-18GW(D). Not cooling. Called in a licensed master plumber. He put freon in. Pressure set at 40. Didn't work. He jumped wired to test compressor. Compressor would not kick in so he replaced compressor with a new one from manufact. After replacing it the sensor lite blinked 4 times and according to manual, this means compressor is not working. Shut down unit from electrical box because there isn't a manual shut off on unit only on remote. Still won't work. Plumber has been here 5 times since unit went on fritz. Heat valve not clicking in. Need to know if there is any help for us or should the unit be junked (Only 3rd summer unit has been used). firstname.lastname@example.org
If the freon is 410a the pressure must be 100-120psi,if it is 22 the pressure must be 45-55psi.you unlucky because hitachi havent problems with compressors.is it inverter the unit?if it is you must check the outdoor pc board,if the 4valve clicking in the you must replaced it propably has stucked.
Posted on Jul 09, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 05, 2014 | Soleus KY-25U Air Conditioner
Aug 18, 2010 | Soleus KFR-18GW Split System Air...
Aug 11, 2009 | Soleus KFR-18GW Split System Air...
Jun 09, 2009 | Soleus KFR-18GW Split System Air...
Jun 08, 2009 | Soleus KFR-18GW Split System Air...
Feb 20, 2009 | Soleus KFR-18GW Split System Air...
Jan 11, 2008 | Heating & Cooling
May 04, 2014 | Hitachi RAS-09UH Air Conditioner
406 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: