Question about Hunter Air Conditioners
The tan/white wire can be insulated/capped and not used. Use and ohmmeter to take a resistance reading between the tan/white wire and L1 & L2. There will be no resistance between the tan/white wire and one of the others. This will be the common wire. Connect it to one side of the contactor. Connect the tan wire to the fan terminal on the contactor and the other wire to the common terminal on the capacitor (that is if you have a 3 terminal capacitor, if you have a 2 terminal capacitor connect tan to one side and the other wire to the other). Then connect the other side of the contactor to the common terminal on the capacitor (on a 2 terminal capacitor connect the contactor to the side that doesn't have the tan wire on it).
Posted on Aug 16, 2010
Tips for a great answer:
Jul 20, 2014 | Air Conditioners
Mar 19, 2012 | Bryant Air Conditioners
Sep 12, 2011 | Hunter Air Conditioners
Aug 09, 2011 | Hunter Air Conditioners
Jul 29, 2011 | Hunter Air Conditioners
Jun 05, 2011 | LG Air Conditioners
Jun 04, 2011 | Hunter Air Conditioners
Apr 07, 2010 | Goodman CKL24AR24 Air Conditioner
Jul 10, 2009 | Goodman CKL60AR60 Air Conditioner
55 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: