Question about Weather King 10AJA3601AH Air Conditioner
There are a few things that can make a gas furnace short cycle when did this problem start and how old is the unit there are a couple of things to try it could be a bad rollout swith they look like little buttons just pull the 2 wires off and connect them to each other you can find them on both side of the burner box jump them out and try it again if this is the problem you can reconnect one at a time starting the furnace after each one to find the bad one then replace . try this first if nothing try jumping out the limit switch it will be in the middle of the furnace looks like a small board with 2 wires connected to it jump it out and start furnace to check.
Posted on Nov 15, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 29, 2014 | Goodman GMS90703BXA Heater
Jan 30, 2011 | Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 11, 2011 | Heating & Cooling
Jan 11, 2011 | York Yankees Bedding MLB Comforter
Jan 03, 2011 | Heating & Cooling
Nov 05, 2010 | Hunter Fan Company 5/1/1 Programmable...
Oct 29, 2010 | Electric Circuit Breaker Kit for Furnace
Oct 13, 2009 | Honeywell Heating & Cooling
Feb 06, 2009 | Carrier Heating & Cooling
Jan 13, 2009 | Heating & Cooling
201 people viewed this question
Usually answered in minutes!