see this causes and fix it. God bless you
Motor Trouble Cause
Electrical Power is Off
Check that all service switches for the equipment are in the "on" position.
Check for voltage at the pump motor or pump controls. If no voltage is found, check for voltage at the electric panel.
If power is on to the building, check fuse or circuit breaker serving the electric motor that won't run.
Check for local reset button on the motor (popped out = off )
Check for other power reset or power off buttons such as an access
door compartment safety switch that turns off power to the equipment
(found on A/C blower compartment doors)
Turn on "off" switches.
Replace bad fuse. Reset circuit breaker; if necessary replace bad circuit breaker.
Let hot electric motor cool down, then push in its reset button.
Be sure all safety interlock switches such as on compartment doors
are depressed and that the doors are securely shut. Replace a bad safety
ELECTRICAL POWER SWITCH FOR HEAT
FAN AUTO ON Thermostat Switch
WATER PUMP ELECTRICAL SWITCHES
CIRCUIT BREAKER FAILURE
ELECTRIC PANEL INSPECTION
Blown fuse, tripped breaker
Replace fuse or breaker - does the pump run and keep running normally?
Be sure proper breaker or fuse size in ampacity is installed - ELECTRIC PANEL INSPECTION
Low voltage to the motor
Check with VOM at the pressure control switch or at the motor wiring
Be sure the proper size of wire is used for the ampacity and length of circuit; Test for low voltage to the building.
Loose, improper, or broken motor wire
Check wiring against the motor installation manual diagram, check all connections for tightness, shorts, burns, damage
Rewire or repair or replace wWhen a sealed compressor motor has "burned out"
this means that the internal wiring of the motor has become
irreparably damaged: the compressor motor windings may be burned and shorted together or shorted to the steel shell
of the motor, or the windings may have burned and simply become "open" or disconnected. If the motor has burned
out in either of these ways it needs to be replaced.