Question about Goodman CKL24AR24 Air Conditioner
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Hi, you will need to replace this thermostat as the circuitry is faulty and keeping the strips energized. The only way to check would be to pull cover from stat and expose stat wires. Power off first. Disconnect the 24 volt hot wire, red and they should shut right off. If so get a new stat. If you need further help, please contact me. Merry Christmas.
Posted on Dec 24, 2009
Check the relay or sequencer that controls the blower if it has one of those. If the fan is controlled by a circuit board then you problem may be there. If it is controlled by a circuit board then you can check for power at the fan connection when the fan is supposed to be on. Then there is always the possibility that you blower motor is burned out. You can use and ohmmeter to check the motor windings. You said you checked the thermostat, how did you do that? If you install a jumper between the R and G connections the fan should run if everything else is OK.
Posted on Nov 15, 2010
SOURCE: Have six year old Bryant
You totally have the wrong motor....you need to get a 208-230 motoro on there for it to work... in fact you probably already have ruined the 115volt motor...the voltage for that motor is to be 115v and you are probably running 130 volts to it...
They probably id not think and gave you a furnace blower motor which would be 115 volts and not a motor for a air handler which runs the higher voltage...
Return it and get the right motor...
Posted on Dec 23, 2010
Tips for a great answer:
Sep 03, 2017 | Goodman Heating & Cooling
Nov 16, 2014 | Heating & Cooling
Dec 16, 2010 | Goodman GMS90703BXA Heater
Nov 02, 2010 | Goodman Heating & Cooling
Jan 04, 2010 | Goodman Heating & Cooling
Dec 16, 2009 | Goodman GMS90703BXA Heater
Jul 06, 2009 | Heating & Cooling
Jun 09, 2009 | Heating & Cooling
Jun 11, 2008 | Goodman Heating & Cooling
241 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: