Question about Goodman GDS80904BNA Open Flame Heater
It sounds like you got a tough one there.When you say the blower starts up and then the igniter comes on are you refering to induced draft motor or main blower. The proper sequence is for the thermostat to call for heat at which point the induced draft motor should come on and run for 30-45 seconds,then the igniter should heat up for a few seconds then gas valve should open and main burner should light. After limit switch reaches set point for fan on ,blower should come on till after heat has reached thermostat setting then burner should go out, and blower run until fan off setting is reached on limit switch. If your furnace is not following this sequence and then not always doing the same thing in the same order,I would recommend that you change out board again. I have had several problems similar to this with Goodman units and all but one time installing new board solved it. That time I did everything I knew to do and talked to factory service techs repeatedly and finally installed new furnace. As far as your question about insulation,. As long as it is fire proof I can't see where it would hurt anything. Sorry I'm not more help. Good luck and thanks.
Posted on Nov 12, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2013 | Goodman GMS90703BXA Heater
Oct 22, 2013 | Goodman GMS90703BXA Heater
Mar 02, 2011 | Goodman GMS90703BXA Heater
Jan 14, 2011 | Goodman GMS90703BXA Heater
Feb 12, 2010 | Goodman Heating & Cooling
Nov 19, 2009 | Goodman GMS90703BXA Heater
Sep 30, 2009 | Goodman GMS90703BXA Heater
Nov 26, 2008 | Goodman Heating & Cooling
Nov 05, 2008 | Goodman GMS90703BXA Heater
325 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: