Question about Ruud UBHC Air Conditioner
To eliminate the t-stat and wiring I would unhook the t-stat wires (of course mark them first) and see if it still does it...
If so, then the problem is interal in the furnace...
then, wiggle wires in the furnace to see if you can isolate the problem to a wire or connection....
My first gut feeling though is that your main circuit board is going bad....I think you will have to replace it...
Posted on Nov 12, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 21, 2015 | Ruud Heating & Cooling
Aug 01, 2014 | Ruud RGTC07ERBGS N/A Achiever 75000 BTU...
Oct 23, 2010 | Ruud Heating & Cooling
Sep 23, 2009 | Ruud UBHC Air Conditioner
Apr 08, 2009 | Ruud UBHC Air Conditioner
Feb 05, 2009 | Ruud UBHC Air Conditioner
Sep 15, 2008 | Ruud UBHC Air Conditioner
52 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: