Question about Intertherm Heating & Cooling
Your furnace will either have circuit breakers or fuses at the bottom in the panel below the blower. Also, there MAY be fuses in the disconnect box outside that gives power to the heatpump. Intertherm furnaces are famous for leaking water onto the left side of the electrical panel in the furnace which is also convieniently where the low voltage transformer is located. If you consider yourself electrically competent, check to see that you are getting 240v to your transformer and if you are the check to see if you are getting 24v out of the transformer. If you can't find the problem in any of these steps, I would recommend contacting a qualified professional to check the system out.
Posted on Jun 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 08, 2015 | Intertherm Heating & Cooling
Jun 15, 2008 | Amana Heating & Cooling
Oct 11, 2014 | Heating & Cooling
May 04, 2010 | 1999 Cadillac DeVille
Nov 28, 2009 | Heating & Cooling
Sep 21, 2009 | Intertherm P3RA-048K Air Conditioner
Apr 11, 2009 | Heating & Cooling
Dec 13, 2007 | Heating & Cooling
236 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: