Question about Goodman CKL42AR42 Air Conditioner
Only two possibilities. Check the fan motor for bearing play. If the shaft moves side to side or the motor is hard to spin then it is time for a new motor (note being able to wiggle the shaft in and out of the motor is normal, even new motors will do this). Other possibility is the run capacitor for the fan. Usually in a/c's they use a dual run capacitor for the fan and the compressor. this will usually be a grey or silver, round or oval cylinder with either two or three terminals on it. If there are three terminals, they will be marked, (C, HERM, and FAN) mark all wires to make sure that they make it back to the same terminal on the new capacitor. If there are only two terminals then it doesn't matter which wire goes to what terminal, but if there are multiple wires going to a terminal, those wires must be kept together on the same terminal. NOTE: the capacitor will need to be purchased from a HVAC service dealer or some place like W.W. Grainger or Johnstone Supply (these are wholsalers and you will need a business afilliation to purchase).
Posted on Jun 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 18, 2013 | Heating & Cooling
Aug 21, 2011 | Heating & Cooling
Feb 01, 2011 | Samsung AS18A6RB Air Conditioner
Aug 10, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Jan 25, 2010 | Heating & Cooling
Aug 19, 2009 | Carrier 38CKC042 Air Conditioner
Jun 22, 2009 | Heating & Cooling
Jun 17, 2008 | Goodman Heating & Cooling
115 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: