Question about Goodman Heating & Cooling
Replaced compressor in 5 ton ac unit. ck for leaks with nitrogen. ran a deep vacum . added freon r 22 to 50 psi pressure before starting. unit ran for about 1/2 hour then stop . Kick out in overload. never fully equalized totally.
thought there might be restricktion in system , ck piston its ok, ck filter in unit its ok . took off high side line set left suction side and ck with nitrogen.
could it be the new replacement compressor bad.
You MUST WEIGH IN THE NEW CHARGE OF R-22. There should be a label on the side of the a/c unit that states what the factory charge was. This is only a starting point. Once you have the factory charge in the system, then turn on the unit and allow it to stabilize (5 min) . Check pressure on low side and check teperature on low side pipe. Temperature of pipe should be 8 to 15 degrees above what the boiling point of the refrigerant is for the current pressure you are reading. If the temperature is more than 15 degrees, add R-22 in 4oz increments allowing 5min in between each time you add until you are in the "zone". When you do this, your head pressure needs to be 225-250. if you need to cover the coil or block the outdoor fan to do this then do it. Hook up the vacuum pump and start over
Posted on Jun 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 16, 2014 | 2003 Nissan Altima
Feb 26, 2013 | Heating & Cooling
May 21, 2011 | Toyota Passenger Cars & Trucks
May 01, 2011 | Heating & Cooling
Apr 04, 2011 | 2000 Chevrolet Silverado
Dec 27, 2010 | Heating & Cooling
Jul 31, 2010 | Goodman CKL36AR36 Air Conditioner
Nov 15, 2009 | Frigidaire Gallery Series GLHS269ZDB 36"...
Jun 26, 2009 | Goodman Heating & Cooling
Aug 25, 2008 | Goodman Heating & Cooling
305 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: