Question about Heating & Cooling
Either your condensate drain is blocked with debris or you've been freezing up. Look for a white pvc pipe usually 3/4" coming out the front of the unit. Find the other end and stick a shop vac on it. If you get a glob of goop followed by water, this was your problem. If you can check the indoor coil, see if there is any ice, if there is ice, check your air filter, if filter is good, call an a/c service because you probably have a freon leak. If ice is an issue, you must turn the system off and turn the fan switch on to allow the system to thaw completely before you can try to use it again or also before an a/c service can repair it.
Posted on Jun 18, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 15, 2013 | Cars & Trucks
Aug 04, 2017 | 1997 Buick Century
Mar 20, 2017 | Heating & Cooling
Jun 13, 2011 | Whirlpool AD35USS Dehumidifier
Jun 01, 2011 | Kenmore Dehumidifiers
Nov 20, 2010 | Ford Windstar Cars & Trucks
Nov 17, 2009 | 2000 Volkswagen Beetle
Jul 22, 2008 | Intertherm Heating & Cooling
May 17, 2008 | Hoover Floormate H3000 Upright Wet/Dry...
Jan 21, 2018 | Heating & Cooling
Jan 21, 2018 | Dometic Heating & Cooling
296 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: