Question about Heating & Cooling
Green flash is the sparking, which is common which elderly contactors. It should likely be replaced. Test for the problem by checking for continuity (ohms) on the solenoid coil of the contactor. (The two small wires on the side.) Test also if you get 24v AC on those two wires when the A/C is turned on. If you have no 24v, it's a thermostat or wire problem. If no continuity, replace the contactor. (Always pull the wires off the contacts when checking the contacts for continuity.)
Posted on Nov 11, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 12, 2018 | Goodman Heating & Cooling
Nov 26, 2017 | Heating & Cooling
Jan 25, 2014 | Goodman Manufacturing Goodman GPH1348H41...
May 11, 2013 | Ruud 3 Ton Split System Heat Pump
Dec 04, 2012 | Hardware & Accessories
Aug 03, 2011 | Heating & Cooling
Nov 18, 2010 | Heating & Cooling
Oct 30, 2008 | Ruud UAMB Air Conditioner
Mar 21, 2019 | Goodman Heating & Cooling
61 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: