Question about Intermatic EJ500C - Indoor Digital Wall Switch Timer - Astronomic Feature
If I understand correctly, you are replacing a switch with the EJ500 timer.
You mention a 'plug'
The EJ500 has 3 wires: Black Red Blue.
If you are replacing a single-pole switch:
The switch has 2 wires, one of these wires is the Hot-from-breaker and the other wire goes to Load:
Timer-black connects to Hot-from-breaker.
Timer-blue connects to wire-going-to-Load.
Timer-red wire is capped off. Red is not used for single pole switch.
If you connect wires and your lights blink, then you put the red wire where the blues wire should go.
If you connect wires and lights do not operate, try reversing the blue and black wires.
I posted images of EJ500 wiring (the Intermatic EJ500 and ST01C have identical wiring
If you are replacing a 3-way switch, the wiring is more complicated.
The EJ500 can not replace a 3-way switch wire-for-wire.
Diagrams on link above show wiring for 3-way.
Add a comment if you need more help.
Posted on Nov 11, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 16, 2015 | Ovens
on Feb 10, 2010 | Televison & Video
Jun 06, 2011 | Televison & Video
Oct 15, 2010 | Bosch Evolution 500 SHE45M05UC Stainless...
May 18, 2010 | Office Equipment & Supplies
Jan 20, 2010 | Maytag Atlantis MDE7400AY Electric Dryer
Oct 05, 2008 | Televison & Video
173 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: