Question about Honeywell Programmable Thermostat Heater
Sounds as though another problem is showing up. Verify T-stat is sending the red 24volts (alt current) through the White wire. This can be done at the t-stat or the furnace whichever is easier to access. At t-stat your meter will show 24volts from red to any wire that the t-stat is not jumping to. So if you put on lead on Red and other on White and 24 shows up the t-stat is not connecting that and the furnace will (NOT) turn on heat. If you get 24 on Y or G but nothing on White then the t-stat is (Good) and the furnace in not kicking on.
To diagnose furnace look for flashing light on board. count flashes and read furnace diagram for info. Furnace diagnosis will take some patience and observation of what happens when. Problems can be Airflow, or parts. It takes some watching. I've found tools jammed in vent stacks, blocked (dirty) evaporators and failing sensors or relays. All causing the units to start but not stay lit.
Posted on Feb 14, 2011
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 02, 2015 | Honeywell RTH6350D1000 5/2Day Prog...
Apr 01, 2014 | Honeywell Digital Round Single Stage...
Mar 14, 2014 | Atwood 38591 Excalibur XT Furnace 1522 15K...
Jan 24, 2014 | Ruud UBHC Air Conditioner
Jun 21, 2017 | Heating & Cooling
Sep 12, 2011 | 2002 Chevrolet Trailblazer Ext
Feb 02, 2011 | Ruud UBHC Air Conditioner
Jan 09, 2010 | Heating & Cooling
Feb 28, 2009 | Honeywell Electronic Programmable...
Jan 04, 2009 | Honeywell Electronic Programmable...
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
170 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: