Question about Ruud Central System Air Conditioner
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I have 2 Ruud Achiever 90 Plus UGRK's. Units were install in 2004. One unit flames' out after ignition just prior to the fan kicking in. Confirmed gas value is functional by switching valves. Check wire connections. Could it be the remote sensor or another 24 volt sensor at the IFC that locks out the gas valve?
Posted on Apr 10, 2008
SOURCE: Clunk noise Ruud Furnace
I had the same problem, the motor shaft and bearings were going bad. There was about 3/16" travel on the shaft that the blower attaches to. I replaced the motor myself and it runs nice and quiet. I have had that noise that you describe for over 8 years, but it got real noisy about a week ago. I talked to the maintance department about it where I work and they said the motor bearings were probably going bad. They were right, I took the motor out of the furnace and they took it to a parts store and got me a new one $270.00 for it. It is a special motor due to the fact that the frame mounts bolt directly onto the motor housing. Make sure if you do this job yourself that you take the motor to the parts store so that they can match it up. The guy at the store told our maintance man if it didn't require the bolt holes in the motor housing it would have been $100.00 cheaper.
Posted on Dec 24, 2008
sounds like you have bad flame sensor or the sensor is in a bad postition. To get eliminate the lockout turn the power off to the unit and back on again. Look at the circuit board light and see what the troubleshooting code is.
Posted on Jan 13, 2009
Sounds like a flame rod issue or the flame is not getting to it in time. The flame rod is located either far right or far left in the burner box and has only one wire going to it. It should be in line with the flame on a burner. The computer allows only a second or two for the all burners to lite and to get to the flame rod. Check the flame travel from burner to burner. You may have to clean the burners, the flame tray to each burner and the flame rod. Also check any electrical connection at the flame rod, circuit board and the grounds to the furnace cabinet.
Posted on Dec 27, 2009
SOURCE: I have a Ruud Silhouette
I had the same problum with my heater to no end. I thought it was the th-sat . still don't know if it was . one of the sencers I was feeling, and the disc snapped in and the heater ran but on heat. turn off power and unplug the power cord and removed the sencer and taped it until it pop back out and when it did I resemble back in place.repluged all back up. turn the heater back on and the flame stayed on . LET THEIR BE HEAT. I played with it for 4 hrs.I don't know if this was the problum .will have a teck look at it to be safe.
Posted on Dec 31, 2010
Tips for a great answer:
Dec 26, 2017 | Ruud Heating & Cooling
Feb 15, 2015 | Honeywell RTH221B1000-OB Open Box Basic...
Feb 03, 2015 | Heating & Cooling
Nov 18, 2014 | Heating & Cooling
Nov 23, 2013 | Source1 CTS Series Model S1-THPU32P7S...
Mar 19, 2013 | Heating & Cooling
Feb 21, 2013 | Bryant Cube Series 1 Stage Heat/ 1 Stage...
Feb 13, 2010 | Ruud UBHC Air Conditioner
Dec 18, 2008 | Ruud UBHC Air Conditioner
297 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: