Question about Carrier 38CKC060 Air Conditioner
Carrier Model 38CKC060370 About two years old and has worked very well during past two summers. Now ... with thermostat set for about 69 deg. ... system runs for about 1/2 hr. and puts out cool air at about. 65 deg at vent ...drops inside temp from high 70s to low>mid 70s ... then stops producing cool air put condenser and fan keeps running. System has to be turned off for a while and started up again to continue producing cool air.
Service company said that condenser was icing up due to stuck bypass ?? They said everything now looks good ... PG&E said power consumption is normal ... but system still only cools for a short while and will not chill house down to or below about 73 deg.
If the refrigerant has been accurately charged and diagnosed, I would look for an air restriction. Check your filter first of all. It sounds like it may still be trying to freeze up. Make sure all the vents are at least a little open and the return grill is not blocked. In the Rocky mountain region we like to see around 44- 50 deg. at the vents. 65 would tell us that everything is not ok.
Posted on Jun 17, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 14, 2015 | Carrier Heating & Cooling
Aug 02, 2011 | Carrier YC273D Air Conditioner Window/Wall
Jul 03, 2011 | Carrier 38CKC060 Air Conditioner
Mar 20, 2011 | 1999 Chevrolet Cavalier
May 10, 2010 | Carrier 38CKC036 Air Conditioner
Jul 13, 2009 | Heating & Cooling
Jun 12, 2009 | Heating & Cooling
Jun 01, 2009 | Ruud UAMB Air Conditioner
Nov 25, 2007 | Heating & Cooling
648 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: