Question about Goodman CKL36AR36 Air Conditioner
If it lights and goes right back out its the flame sensor if it dont lite at all check all of your rollout and limit switchs ( they look like buttons) just jump them out with a jumper wire also you can jump out the gas valve to see if it works by putting a jumper wire ( small section of wire with alligator clips on both ends ) from the red terminal screw on the low volage side to the m1 terminal it will click open if it works , make sure the door switch is closed so you can have power while testing . do not try to leave furnace on with jumpers in it will burn your house down !!
Posted on Nov 15, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 20, 2011 | Goodman Heating & Cooling
Jan 27, 2011 | Goodman Heating & Cooling
Mar 05, 2010 | Goodman GMS90703BXA Heater
Jan 26, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Jan 10, 2010 | Goodman GMS90703BXA Heater
Dec 13, 2009 | Goodman Heating & Cooling
Nov 28, 2009 | Goodman Heating & Cooling
Nov 19, 2009 | Goodman GMS90703BXA Heater
Nov 18, 2009 | Goodman GDS80904BNA Open Flame Heater
Dec 05, 2008 | Goodman GMS90703BXA Heater
60 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: